copper conductor PVC insulated steel wire armoured 95mm power cable
Standard and Scope of Application
The power cable can be produced and supplied according to
IEC60502,also can manufacture the products that are based on BS and
other standards.In addition,under customers’ requirement,we can
design and manufacture the products that have special
performance.The power cable are used in fixed laying on
transmission and distribution electrical lines of 50HZ AC rated
voltage up to 6kv.
Property for Using
The long-time permissible working temperature of cable conductive
core is not more than 70°C.
During short circuit(max.lasting time is not more than 5
seconds),the max.temperature of cable conductor is not more than
They have good chemical stability,and properties of acid
resistance,alkali resistance,salt resistance and flame resistance.
Technical Requirement(Type and Name)
|VV(VLV) Copper(Aluminum)Conductor PVC Insulated and Sheathed Power
|VY(VLY) Copper(Aluminum)Conductor PVC Insulated,PE Sheathed Power
|VV22(VLV22) Copper(Aluminum)Conductor PVC Insulated,STA,PVC
Sheathed Power Cable|
|VV23(VLV23) Copper(Aluminum)Conductor PVC Insulated,STA,PE Sheathed
|VV32(VLV32) Copper(Aluminum)Conductor PVC Insulated,SWA,PVC
Sheathed Power Cable|
|VV33(VLV33) Copper(Aluminum)Conductor PVC Insulated,SWA,PE Sheathed
Nominal Cross Section of Conductor Core
Nominal Thickness of Insulation
1. Standard of XLPE Cable: According to GB12706( Equal to IEC60502)Also can do by standard
of ASTM,BS,DIN and AS/NZS or other standards as request.
2. Rated Voltage of XLPE Cable:
3. Construction of XLPE Cable:
Conductor:Copper or Aluminum
Inner sheath:PVC or PE
Armoured:Galvanized steel tape,Galvanized steel wire
Outer Sheath:PVC or PE
NO. of cable cross: 1 core(Single core),2cores(Double
cores),3cores, 4cores(4 equal-section-area cores OR 3
equal-section-area+1 small section area neutral core),5cores(5 3
equal-section-area cores+2 small area neutral cores OR 4
equal-section-area +1 small area neutral cores).We provide armored
type and non-armored type for the cables stated above.
Also can do according to the customer's request.
4. Characters of XLPE Cable:
a.Max Long-time operating temperature of XLPE insulated cable is 90°C
b.Installing temperature of cable should not be less than 0°C
c.Max short-circuit temperature is not exceed 250°C,Not more than5
d.Unable be laid without the limit of fall with enough mechanical
pull,Single core cable can not be laid in iron tube or fixed by
circled iron tools around cables
Drawing of PVC insulated PVC jacket Power Cable
Wooden drum or wooden&steel drum;
Your requested way of packing.
1. 15 years experience as professional manufacture.
2. Strict and complete test procedure to ensure the quality.
3. Quick delivery time.
4. More competitive price in this field.
5. Abundant experience for exporting, SGS inspection, taking in a
Welcome to visit our company & factory, We are always here for you.
always for your best services
Contact person : Ricky Zhao
Mob/WhatsApp: 86-158 3806 2790